› M1 Support Forum › M1G and ELK-110(v5) – how do I get separate Fire, Burglar and CO alarms? › Reply To: M1G and ELK-110(v5) – how do I get separate Fire, Burglar and CO alarms?
You will need to make the following connections and programming changes: * Connect the RED Wire of the 110v5 to constant +12 VDC. With a 8Î© load the 110v5 will draw 1.2 Amps and 800 mA if in Millimiser Mode. You may need a secondary power supply. * Connect the BLACK Wire of the 110v5 to the Negative of the power supply. If you do use a secondary power supply you will need a Common DC Negative between the Power Supply NEG and a NEG terminal on the M1. * Connect the BROWN Wire of the 110v5 to Output 2 “-” (Negative). * Output 2 Must be programmed as a Voltage Output — Globals G26 * Either connect the WHITE Wire of the 110v5 to an Output on J16 of the M1 (for example Output 16) or to the Normally Open N/O of Output 3 on the M1. * If you use Output 3 you will need to connect the COM to +12 VDC on the power supply. * Write your Rules Whenever the CO Alarm in My Home (Area 1) Turns ON Then Turn Output 16 ON —- At this point you can turn Output 16 On until another rule turns it off or have it timed Whenever My Home (Area 1) Becomes Disarmed Then Turn Output 16 OFF Output 2 on the M1 will turn ON steady for Burglar and Carbon Monoxide Alarms. A Fire Alarm will cause Output 2 to Pulse. If the 110v5 detects a Steady Input on the BROWN and WHITE Wire it will Speak the Carbon Monoxide Message and produce the Temporal 4 Buzzer Sound