Thanks Brad. I figured out the issue that it wasn’t in the elk system side it was the configuration of the somfy shade along. The installation manual on their end didn’t clearly explain how the communication happens. For all of those that may read this post you have to rotate the selector switch initially to program the shade. However, when it is communicating with the M1XSP the selector switch has to be put back to what the address is. In this case the text string of 0103U which I used, the address is 01 and the channel is 03. So I need to change the selector switch back to 01 to have it communicate with the elk system.